Remove scale from lines and clear clogged drains easily and effectively with Calci-Solve. The product includes a special inhibitor that coats the inside of the pipes with a protective film, allowing the acid in Calci-Solve to quickly dissolve calcium, magnesium, sodium, lime, rust and other such elements without harming pipes.
Use Calci-Solve to remove scale and rust from the following:
Packaging Size Part Number
1 quart bottle 4134-24
1 gallon bottle 4134-08
This product must be used in accordance to the following directions by HVACR professionals only.
HOT WATER COILS: Attach a stand pipe and pour a solution of 2 parts water and 1 part Calci-Solve. If coil is completely stopped use Calci-Solve full strength.
HOT WATER HEATERS: GAS TYPE. Break at unions leading in and out of heater. Drain water. Use solution of 2 to 5 parts water and pour in enough solution to cover bottom of heater to a depth of one foot. Flush thoroughly before returning to use.
ELECTRIC HEATER: Cover coils with a solution of 5 parts water and one part Calci-Solve.
BOILERS: 10 to 15 parts water and 1 part Calci-Solve. Allow to work for at least 12 hours. Extra flushing may be required to remove loose sediment left on bottom.
HOSPITAL STERILIZERS: OPEN TYPE. Cover heating coil with solution of 2 to 5 part water, 1 part Calci-Solve. CLOSED TYPE. Submerge coils in solution 2 parts water, 1 part Calci-Solve. Flush thoroughly before returning to use.
WATER METERS, VALVES AND STEAM EQUIPMENT: Submerge parts to be cleaned in solution of 2 to 5 parts water, 1 part of Calci-Solve.
UNIT HEATERS: Fill steam or water coils with solution of 2 parts water, 1 part Calci-Solve. If circulating pump is used, use 5 parts water, 1 part Calci-Solve.
Download the product bulletin and other relevant literature here.
Download a low resolution file of the product label here.
SDS and RTK Information
Read and understand the product’s Safety Data Sheet for precautionary and first aid information.
calci-solve; Calci Solve; calci solve; CalciSolve; calcisolve